This property owner was relieved to have a working hot water system
The Nu-Trend plumbing team was called to try repair a hot water system that wasn’t working very well in Sydney. They were having all kinds of hot water issues in their property that other plumbers weren’t able to find a solution for. A number of years ago they were experiencing mixed hot and cold water, when they would only turn on the cold water tap, yes, hot water water would be coming out of the cold tap.
The property owner had called a plumber and they tried to fix it, but the plumbing issue persisted, in fat it returned within a few days. Over time, they tried another four licensed plumbers, but sadly they had been experiencing the same hot and cold water issue with their hot water system for many years.
The property was a mansion that had a commercial grade plumbing set up similar to a large city building. It had a plant room with plumbing that had hot water circulating pump system. This made isolating any issues even more difficult than normal. There could be all kinds of pipes or things installed in rooms or hidden wall valves with pumps etc.
How did we find the hot water system problem?
On inspection we found a Spring Check Valve installed but it should have been a Swing Check Valve.
The Swing Check Valve had been replaced, so the property owner and every other plumber assumed it wasn’t the issue, but, this type of valve is actually not designed for commercial hot water set ups and was obviously failing due to the mechanical set up of the valve.
The return line always stays hot for instant hot water hence it causes the springs to fail in a Spring Check Valve. It’s actually a legal requirement to install the right valve, it’s not necessarily a dodgy plumbing job, but it’s just a job that should have been done with a little bit more knowledge and care.
This is why it is so important to choose a licensed plumber like Nu-Trend that has plenty of experience working on residential or commercial sites to work on plumbing in Sydney.
So in this instance a Swing Check Valve needed to be installed to prevent the loss of hot water, back charge and the cross connection then prevents dead legs. What was happening with the use of the wrong valve was that the hot water was back charging through the cold water line of the house.
This should have been a simple repair by the first plumber that looked at it.
READ OUR FREE GUIDE
Local | Licensed | Insured
HOME OWNERS INSURANCE
Protection for home owners.
Local Sydney contractors.
FULLY LICENCED 217859C
A qualified and licensed renovator.
Public liability insurance for peace of mind.
Drainer | gas fitter | plumber | renovator
Nu-Trend is a Sydney company with more than 15 years experience completing bathroom renovations & solving plumbing problems. he Directors Rob and Rick are hands-on, and provide a personalised service.
STANDARDS AUSTRALIA AS/NZS3500:2018 Compliant
All the work carried out by Nu-Trend is AS/NZ3500:2018 compliant. It is the Australian Standard for Plumbing and Drainage in NSW as set down by Standards Australia and the Australian Building Codes Board. They give the plumbing industry technical direction to enable compliance with required regulatory frameworks.
15 years experience with a written commitment.
Rick and Rob are the hands-on directors for Nu-Trend. Rather than hire sub-contractors and manage their business from a distant office, they are on the tools, at your site & working towards delivering your bathroom renovation or plumbing service. It means you are talking directly to the owners of the business, the guys who are accountable and responsible rather than via email or through customer service teams.
It is why they are able to provide a written guarantee that demonstrates their confidence in standing by the quality of their workmanship and the service they deliver to every single client.
They have a very single minded commitment to deliver a high level of professionalism and quality, they’ve been doing renovation contracting in Sydney for 15+ years.